Plumbing - Recent Questions, Troubleshooting & Support
How to disable moine faucet
Can you tell us more about what you mean by Disable?
If you mean,how can you stop water from flowing, there are usually shutoff valves in the hot and cold water supply lines under your sink (nothing to do with the faucet itself).
on Nov 18, 2019
My moen 7200 side sprayer needs to be replaced. How do I disconnect the under the sink hose?
First clean out your cabinets under the sink. Second turn turn the cold water valve off, hot water valve as well.
You should be able to locate the sprayer hose as it will have a weight on it, this helps to pull the sprayer back when you are finished with it. Remove the weight by lifting up on the tab should be on the center of the weight.
Then you should see the hose connection.There you should see a button.Push it in and give it a little tug. The hose should be disconnected. Just follow in reverse order to reinstall.
I hope this is information is helpful. Have a blessed day.
on Nov 06, 2019
I replaced my pressure switch with one that has a emergency low pressure off switch.
There are a lot of variables. Are you on a shallow well pump? It sounds like the well doesn't make much water. Check your well tank pressure. With 0 psi of water (drain the pressure) There should be 2 psi of air less than than the start up. If the pump is set to start at 30 psi, there should be 28 psi of air in the tank. It sounds to me like either the tank is shot, or the pump doesn't make much water. If you leave a faucet on while putting air in the tank and air comes out the faucet, then, the bladder is shot.
on Oct 30, 2019
Not finding what you are looking for?